Hydrophors Pressure Setting / Switch / Relief / Pressure / Hydromate hydrophors
The hydrophor pressure setting is removed by opening the cover on the pressure switch with a screwdriver in order to change the original pressure settings.
This type of hydromate hydrophor is operated while the taps are closed. After the relieved pressure reaches the upper pressure and the device stops, one of the taps is opened and the pressure at which the device starts to operate (lower pressure) is observed from the manometer.
The hydrophor pressure switch is adjusted according to the type with the related screws, the lower and upper pressure. According to the adjusted new pressure value, the pre-gas pressure of the membrane tank is measured and readjusted to be 10% lower than the lower pressure.